Eldor Corporation, Izmir, Turkey
The Eldor Corporation management decided to find a solution to the problems with differences in indoor temperature, which were damaging PLC print cards in its production facilities.
FabricAir, together with Cosar Muhedislik (the Contractor), designed a FabricAir dispersion system using Combi 20 fabric with NozzFlow™ that minimized the differences in indoor air temperature. The new system is able to sustain an average room temperature of 25-26°C (compared to 40°C in the past) with αT of max 2° in the whole production area.
The retrofit of the air distribution system from conventional sheet metal ducts with spot diffusers to a FabricAir air dispersion system has completely resolved the problem of PLC print cards burning out.
“Considering that there is no more disruption to production and the cost of new PLC cards, the investment in the FabricAir air dispersion system has paid for itself in very short time”, says Mr. Tolga Yücel, Deputy Technical Manager at Eldor Corporation.